Another booster set replaced and the client is all the better for it.
Original unit was plagued with problems, restrictive and poor suction pipework, excessive dead leg on the discharge manifold and years of all three pumps running day and night. The single pressure transducer had packed in long ago and the pumps were running all the time. This meant the pumps were at maximum pressure and leaks were more likely.
Subsequently the pipework was also getting warm overnight, rather than seeing the pumps switch off and therefore providing an avoidable legionella risk.
The client now has lower energy costs, no single points of failure, a new unit that is covered by our 24/7 warranty coverage for 2 years and we will then service and maintain it for them. What’s not to like?
If you require any assistance with booster sets, tanks and pressurisation. Please contact us anytime.